Back to Top
Replace the thermocouple
No hot water? If you have a natural or propane gas water heater, chances are the pilot has gone out. The pilot is a small flame that ignites the gas burner on your waterheater. When it goes out, first try relighting it, following the directions on the water heater label. If the pilot doesn't relight, or if it goes out right after lighting, by far the most common cause is a bad thermocouple. The good news: You can usually replace a thermocouple for minimal cost and in less than an hour. You'll get your hot water going without waiting for a pro to show up and save the cost of a service call.
To replace the thermocouple, follow the photo series. Be sure to turn off the shutoff valve in the gas line; that is, one quarter turn so that the handle is at a right angle to the pipe. Since working room is tight around the burner, we recommend that you simply unscrew the three nuts at the control valve and pull out the entire burner assembly. You'll see either a slot or clips that hold it in place (Photo 2). Then either unscrew the thermocouple end or pull it out (depending on the water heater) and take it with you to an appliance parts store to find a match. Position it exactly like the old one. When relit, the pilot flame should wrap around the thermocouple bulb.
To reattach the three lines to the gas valve, thread the nuts into place with your fingers and hand-tighten them. Then snug them up with a quarter to half revolution with a wrench. The metals are soft, so don't over tighten.
Be sure to test for gas leaks. You must have the pilot lit and the burner on for this test so that gas is flowing through the large tube. Reopen the shutoff valve, relight the pilot, then turn the control valve to “on”. When the gas burner comes on, use a 50/50 dish
soap/water mix to test the screw joints for air bubbles that indicate leaks.
When Not to Replace the Thermocouple
Some gas water heaters have a “closed” burner chamber, which is difficult to access. We recommend that you call a service pro to fix this type. Also, some gas
water heaters don't have pilots. Let the
pros fix these as well.
You should not be able to smell gas during this operation (except for a slight whiff when you remove the gas lines). If you do, leave the house
and call your gas utility.