Remove the old rod
1 of 2
Photo 1: Remove the old anode rod
Loosen the hex head with a short burst from your impact wrench. Unscrew it by hand once it's loose.
2 of 2
Photo 2: Install the new anode rod
Coat the threads with pipe dope and slide the new rod into the tank. Tighten with a socket and ratchet by hand.
Most water heater tanks are steel with a thin glass lining to protect the metal from corrosion. Since the lining eventually cracks, tanks have a second line of defense against rust: a long metal “anode rod” that attracts corrosive elements in the water. When the rod
itself becomes so corroded that it can no longer do its job, the tank soon rusts out, leaks and needs replacement. However, if you replace your anode rod before it fails,
about every five years, you can double the life of your water heater.
Rods are made from magnesium, aluminum or aluminum/zinc alloy. Aluminum replacement rods are sold
at home centers. In most cases, the hexagonal head of the rod is visible on the top of the water heater. If you don't see the hex head, check your owner's manual. The
rod may be under the water heater's sheet metal top or connected to the hot water outlet nipple. (A few newer plastic-lined tanks have no anode rods to replace.)
Before you get started, close the shutoff valve, turn on the hot water at a faucet to relieve pressure, and turn off the electricity or gas to the heater. Open the drain
valve near the bottom of the tank and drain out several gallons of water. Caution: The water is hot!
Drain some water from the
tank to check for rust. It’s time
for a new water heater if you
see rusty flakes (not just orange
water, which can come from
corroded pipes or well water). If
the water is clean, remove the
rod to check its condition.
To loosen the rod, you’ll
need an air compressor, a
1/2-in.-drive impact wrench
and a 1-1/16-in. socket. If you
don’t have an impact wrench,
go buy a cheap one for about
$30. Even with a breaker bar, it
can be nearly impossible to
break the anode rod free.
Turn off the power or gas.
Then close the cold-water
valve at the top of the tank
and drain off several gallons.
Loosen the hex head with the
impact wrench, but unscrew it
the rest of the way by hand.
Hint: The hex head may be
under a plastic cap. Uncover
it, then pull it up and out to
check its condition (Photo 1).
Buy a new anode rod at a
home center or online (see
sources below). Install a flexible
rod if you have less than
44 in. of clearance above your
heater (Photo 2). Turn on the
water, the power or gas, and
burp the air from the system.
Check the condition of your anode rod every three years.
If the hex head is set below the top of the heater, you'll need a 1-1/16-in. socket to reach it. If it protrudes above the top, you can use any type of wrench. Chances
are your old anode rod will be frozen in place by corrosion. Douse the head with a spray lubricant such as WD-40 and give it a few minutes to penetrate. You may also have to slip a “cheater” pipe over the
wrench handle to increase your torque. The weight of the water in the tank is usually enough to keep the entire heater from turning. But if it begins to move, have a helper (or two) hold it in place.
When the threads break free, stop turning and look for water around the hex head. If you see leakage, drain the tank further. If you don't have enough overhead
clearance to pull the rod out of the tank, bend it as you remove it. Then when you buy a new rod, choose a flexible, “segmented” version. Smear Teflon pipe thread sealant on the threads of the new rod before you install it. Don't use tape, since it can reduce the
effectiveness of the rod. Before you turn on the water and
electricity or gas, drain another gallon out of the tank to flush out any remaining debris.